What is Arc Flash?
Simply explained, an arc flash is a flashover of electric current (usually in the form of an explosion) that occurs when the energy properly contained in electrical equipment, suddenly leaves the equipment and travels through the air, either from one live conductor to another, or from a piece of energized electrical equipment to ground.
Visit Our AF Course Page:
The results of such a flashover are in most cases violent and when an electrical worker is in close proximity to the electrical equipment that is involved in an arc flash, that worker can receive a serious injury and sometimes, even death can occur.
Arc flash is usually caused by a number of factors, including:
The following three factors dictate the severity of an arc flash injury:
Arc Flash explosions are costly. It is because of the extreme nature of an arc flash explosion that electrical workers are injured. And when they are injured, the results can be devastating, even resulting in death. Many injured electrical workers discover that their quality of future life is impaired and they can never regain their past quality of life. Extensive medical care is often needed, sometimes resulting in medical bills exceeding $1,000,000.
The National Fire Protection Association (NFPA) has developed a standard (NFPA70e) which outlines specific approach boundaries that are designed to protect electrical workers near energized electrical equipment.
Here are the Arc Flash Boundaries:
Flash Protection Boundary (outer boundary)
The Flash Protection Boundary is the farthest established boundary from the energized electrical equipment which contains a hazardous level of incident energy. If an arc flash occurs within this boundary, a worker would be exposed to a curable second degree burn (1.2 calories/cm2 ). The real issue within this boundary is the heat that is generated from the arc flash, which results in a burn.
The Limited Approach Boundary is defined as an approach limit at a distance from an exposed live part where a shock hazard exists.
The Restricted Approach Boundary is defined as approach limit at a distance from an exposed live part which there is an increased risk of shock.
Prohibited Approach (inner boundary)
The Prohibited Approach Boundary is defined as a distance from an exposed part which is considered the same as making contact with the live part. This distance is not common between equipment. Some equipment will have a greater flash protection boundary while other equipment will have a lesser boundary.
Ways to Protect the Workers
There are a number of important ways that workers can be protected from an arc flash hazard. Some of the ways are suitable for the protection of qualified electrical workers doing work on energized electrical equipment and other ways that are intended to protect non-qualified electrical workers who work on nearby energized equipment.