Wednesday , 18th Jan 2017
× Home Channels News Electrical Training Buyer's Guide EF Partner Media
Content Community Connection

# When To Use A StepDown Transformer

#### Step Down Transformers Designed To Reduce Voltage

Step down transformers are designed to reduce electrical voltage. Their primary voltage is greater than their secondary voltage. This kind of transformer "steps down" the voltage applied to it. For instance, a step down transformer is needed to use a 110v product in a country with a 220v supply. This kind of electrical transformer are made from two or more coils of insulated wire wound around a core made of iron. When voltage is applied to one coil (frequently called the primary or input) it magnetizes the iron core, which induces a voltage in the other coil, (frequently called the secondary or output). The turns ratio of the two sets of windings determines the amount of voltage transformation. An example of this would be: 100 turns on the primary and 50 turns on the secondary, a ratio of 2 to 1.

This kind of electrical transformer can be considered nothing more than a voltage ratio device. With this type of transformer, the voltage ratio between primary and secondary will mirror the "turns ratio" (except for single phase smaller than 1 kva which have compensated secondaries).

A practical application of this 2 to 1 turns ratio would be a 480 to 240 voltage step down. Note that if the input were 440 volts then the output would be 220 volts. The ratio between input and output voltage will stay constant. Transformers should not be operated at voltages higher than the nameplate rating, but may be operated at lower voltages than rated. Because of this it is possible to do some non-standard applications using standard transformers.

A Single phase transformer like this, 1 kva and larger, may also be reverse connected to step-down or step-up voltages. (Note: A single phase step up or step down transformer sized less than 1 KVA should not be reverse connected because the secondary windings have additional turns to overcome a voltage drop when the load is applied. If reverse connected, the output voltage will be less than desired.

Read Our Other Transformer Pages: Potential Transformer Explained, Control Transformer Explained, Current Transformer Basics, Dry Type Transformers Explained, Isolation Transformer Explained

### EF PartnerMedia

World Class Accuracy - Now in the USA

Introduction to: Calisto2 Instructional Videos

Calisto 2 Installation - Instructional Video

Calisto 2 Troubleshooting - Instructional Video

Spectrum Industries, Inc

Powerful Tools for Electrical Power Systems

SISCO, Inc.

Fault Current & Arc Flash Software and Apps

Catalogs
• 1
• 2
• 3
• 4
Brochures
Specs Sheets, Manuals
Coming soon..

Whitepapers
Coupons
Coming soon..

Articles
• 1
• 2
• 3
• 4

• 04/01/16
• 11/19/12

Top